I have a large quantity of SRT 3000's currently deployed in my organization. They have a combination of AP9630 and AP9631 cards installed. I use the AP9631 card temperature probe to monitor the rooms. I have found a number of devices where the temp probe is not attached. I am trying to do a audit of of the NMC's cards with SNMP. I have figured out the OID to see what port the Temp probe is attached to but I get the same response from a 9631 cards without a probe as I do from a 9630 card. I am trying to find a OID that would tell me the model number of the NMC card so I can figure out which ones I need to have someone visit. With over 2000 devices logging in manually would be challenging.
I have made some progress. snmputil.exe get 10.245.57.65 SNMP_comm .126.96.36.199.188.8.131.52.0 returns the details below. It includes the model number but is not specifically the model number. I guess I can pull it from the string unless someone know the OID that will give just the NMC model.
Variable = system.sysDescr.0
Value = String APC Web/SNMP Management Card (MB:v4.2.9 PF:v184.108.40.206 PN:apc_hw21_aos_220.127.116.11.bin AF1:v18.104.22.168 AN1:apc_hw21_su_22.214.171.124.bin MN:AP9641 HR:5 SN: ZA1937012533 MD:09/13/2019) (Embedded PowerNet SNMP Agent SW v2.2 compatible)
maybe a workaround : 126.96.36.199.4.1.3188.8.131.52.184.108.40.206
it contains the S/N. I suppose AP9630/AP9631/AP9640 are not in the same range.
Choose a location