I have an apc 9631, it was on old firmware ,when i update it the webpage it says "no ups found".
My UPS : SURTD5000XLI
It looks like you have upgraded the NMC firmware with the one for the 3 Phase Symmetra rather than for the Smart UPS UPS.
Her is the firmware you need.
Thanks Matt ( Problem Solved )
Choose a location