Long time reader, have not posted anything as of yet on the forum. I have a question now that I cannot seem to find an answer for at all.
I have had and used, for many years an APC Smart-UPS 1000I NET with serial number GS9814430025. For reference, it has an AP9631 NMC2 Rhodes in it. I recently had to replace the batteries, as the cells that were in the unit started going towards the end of their useful life. In replacing the batteries, I reset the battery constant values in the EEPROM, and somehow pressed the dreaded Ctrl-Y in the tty session, clearing the EEPROM.
I was, subsequently, able to restore the values of the EEPROM, at least as far as I can pick up, correctly. And herein the question. Would anyone that have one of these units be able to extract the EEPROM values for me from their unit, for verification, please? I would be interested in comparing the values of a SUA 1000I NET also, as I think these values may be close or the same.
Here are the values that I currently have captured (as extracted with APCUPSD):
"1) Query the UPS for all known values2) Perform a Battery Runtime Calibration3) Abort Battery Calibration4) Monitor Battery Calibration progress5) Program EEPROM6) Enter TTY mode communicating with UPSQ) Quit
Select function number: 1
I am going to run through the series of queries of the UPSthat are used in initializing apcupsd.
Simulating UPSlinkCheck ...Wrote: Y Got: SMAttempting to use smart_poll() ...Sent: Y Got: SM Good -- smart_poll() works!.
Going to ask for valid commands...Wrote: a Got: 3.?=.-789>@ABCDEFGKLMNOPQRSUVWXYZ'abcefgjklmnopqrsuxyz~Protocol version is: 3Alert characters are: ?=Command characters are: ^A^N^Z-789>@ABCDEFGKLMNOPQRSUVWXYZ'abcefgjklmnopqrsuxyz~
Now running through apcupsd get_UPS capabilities().NA indicates that the feature is Not Available
UPS Status: 08Line quality: FFReason for last transfer to batteries: SSelf-Test Status: NOLine Voltage: 231.4Line Voltage Max: 231.4Line Voltage Min: 230.1Output Voltage: 231.4Batt level percent: 079.0Batt voltage: 28.14UPS Load: 000.0Line freq: 50.00Runtime left: 0287UPS Internal temp: 028.8Dip switch settings: 00Register 1: 00Register 2: 00Register 3: 00Sensitivity: HWakeup delay: 000Sleep delay: 020Low transfer voltage: 196High transfer voltage: 253Batt charge for return: 00Alarm status: NLow battery shutdown level: 02UPS Name: UPS_IDENUPS Self test interval: 336UPS manufacture date: 04/01/98UPS serial number: GS9814430025Date battery replaced: 12/09/19Output voltage when on batteries: 230Nominal battery voltage: 024Percent humidity: NAAmbient temperature: NAFirmware revision: 60.9.INumber of external batteries installed: 000Number of bad batteries installed: NAUPS model as defined by UPS: SMART-UPS 1000UPS EPROM capabilities string: uD43132135138129uM43229234239224uA43110112114108uI43253264271280lD43103100097106lM43177172168182lA43090092081085lI43196188208204e44200155090oI43230240220225oD13115oJ13100oM13208s441HMLLq44202050710p443020180300600k4410TLNr443000060180300E443336168ON OFFThe EPROM string is 253 characters long!Hours since last self test: NA
That is all for now."
I attach here the following:Image with model and serial numbersImage of front of unit
TL;DRWould anyone that have one of these units be able to extract the EEPROM values possibly for me from their unit, for verification, please?
Choose a location