I just noticed that my SUA1000 transfers/trims below the setting. The high setting is on 130V.
Highest voltage measured with voltmeter at outlet (with UPS plugged in): 126V.
I see that the highest voltage in data log is 128.1V. Yet the UPS transfers/trims.Not sure why....
please take into a consideration the value in log is informational only (and shouldn't be compared with a proper oscilloscope measurement). The voltage from your grid could arise above to 130V slightly or for a very few periods that ups will trigger, but not logs...
I am also measuring with a precession voltmeter that has peak feature. Did not reach 130V while UPS is switching over. I guess I could increase to 131V...
I notice the same thing on a SMT1500i. The AVR will kick in 3V below what I set for the High Transfer Voltage.
The voltage the UPS reads from mains input is also about 1V higher than that measured by a quality true-RMS multimeter.
Choose a location