Note: No new discussion posts are allowed in this area. Historical content is for viewing purposes only. NetBotz are actively supported at its own standalone community - https://help.ecostruxureit.com/questions
Yes you can configure the 550 to shutdown outlets on a pdu. This kbase discusses the required cables and firmware http://nam-en.apc.com/cgi-bin/nam_en.cfg/php/enduser/std_adp.php?p_faqid=9299
Be aware that with the netbot connected to the pdu via serial, only the netbot will have access to the device, since the serial port takes priority over telnet and web access. Also there is a known issue with multi-bank pdus. Hope this information helps.
Thanks for the reply that is exactly the information I needed.
This knowledge base article no longer exists but I think I need this exact information. Anyone able to help me?
This kbase should be back up in the next 24-48 hours, I would recommend checking back in the next day or two.
I have a netbotz550 monitoring lab environments in our office building. I was wondering if it is possible to have the netbotz monitor shut down power to our APC switchable pdus if the temp gets to a set parameter? I am new to this system so please bare with me.
Choose a location