Hi, I want to know if a SY200K250D can be expanded to a 250kVA/KW configuration and what modules would I have to add?
Or do I have to change frames and go with the SY250K500D?
So long as your site wiring was for the 250kw load, it should have two empty slots for 25KW modules.
Yes i can be expanded upto 250kVA/KW . But if your load will be between ( 225-250KVA/KW) then it will not be internal redundant.
You simply need to add SYPM25KD Qty 02/-
Here is link for more information
Thanks for your reply.
Do I need to add any battery modules?
You should have at least 1.6 batterymodules (1 module = 1 row = 6 units) per powermodule.
So, 10 powermodules require minimum 10 x 1.6 = 16 modules = 2 full battery frames.
Choose a location: